Views:6 Author:Site Editor Publish Time: 2021-07-12 Origin:Site
Abstract: This article introduces the low-voltage system of Inner Mongolia Meng Niu Dairy (Group) Co., Ltd. to transform the power monitoring system, using smart power meters to collect various electrical parameters and switching signals at the distribution site. The system adopts the method of on-site networking. After networking, it is remotely transmitted to the background. The Acrel-2000 power monitoring system realizes real-time monitoring and management of power distribution circuit power in the distribution room.
With the development of social economy, the improvement of production automation, the liberation of labor and the improvement of quality of life, a large number of electric power-driven equipment is put into production and life, and people's dependence on electricity is getting higher and higher. The reliability and continuity of power supply have become one of the important issues of concern to the entire society. Since the power supply system has the particularity of simultaneous production and consumption, monitoring the entire power supply process is an important means to ensure the reliability and continuity of power supply.
Inner Mongolia Meng Niu Dairy (Group) Co., Ltd. is located in Dangyang City, Hubei Province. There is a power distribution room on site.
This project mainly involves network multi-function meters, microcomputer protection and other equipment in the power distribution room of Inner Mongolia Meng Niu Dairy (Group) Co., Ltd. The monitoring host is located in the duty room on the first floor.
1 Demand analysis
To ensure the statistics and analysis of electricity load for production management and real-time monitoring of dangerous sources. Real-time online monitoring of voltage, current, power and other parameters in the power distribution room at the project site is required. Once the monitoring point is monitored with abnormal parameters, it can detect and alarm in time, and relevant personnel can take necessary measures to avoid safety accidents. The automatic meter reading function saves manpower and material resources, and the power trend curve function can intuitively display the working status and time of each circuit, which is convenient for users to find abnormal power circuits and rectify them in time, and establish a multi-level electric energy measurement system to provide energy analysis basis .
Acrel-2000 system is based on the actual situation of the low-voltage system of Inner Mongolia Meng Niu Dairy (Group) Co., Ltd. to transform the power monitoring system on site. The overall network structure uses shielded twisted pair to directly connect to the data collector and then send the data to the power distribution room for monitoring The host ensures the stability and real-time transmission of the power monitoring system.
1） Control Centre
The control centre is the direct window of human-computer interaction for the management personnel of the power monitoring system. In Inner Mongolia Meng Niu Dairy (Group) Co., Ltd. low-voltage system transformation power monitoring system project, it mainly refers to the monitoring host located in the power distribution room on the first floor.
The network is mainly composed of collectors, Ethernet devices and bus networks. The main function of the serial server is to monitor on-site intelligent instruments; the main function of Ethernet equipment and bus network is to realize the data interaction between the substation and the main station, so that the management of the distribution system is centralized, informatized, and intelligent, which greatly improves The safety, reliability and stability of the power distribution system have achieved the goal of unattended operation.
The device layer is the data acquisition terminal, which is mainly composed of smart meters. The smart meters are connected to the communication server through the shielded twisted pair RS485 interface and the MODBUS communication protocol bus connection. The communication server reaches the monitoring host of the power distribution room for networking. Realize remote control.
System structure diagram
3 System Function
The real-time monitoring system diagram of the substation is the main monitoring screen, which mainly monitors the operating status of all circuits in the substation in real time. Red represents closing and green represents opening. In the system diagram, you can intuitively see the operating parameters and status of each incoming and outgoing line, and you can see all the conventional power parameters on the outlet side of the transformer, such as: three-phase voltage, current, active power, reactive power, and power factor , Frequency, active power, etc. As shown below:
The remote signaling and remote measurement alarm function mainly completes the monitoring of the switch operation status of the low-voltage outlet circuits and the load incoming line. The pop-up alarm interface for switch displacement and load limit violations indicates the specific alarm location and sounds the alarm to remind the duty personnel to deal with it in time. The load limit can be set freely under the corresponding authority.
The event alarm recording function mainly completes the recording of the alarm information and the occurrence time of the alarm information that occurred during the query period, and provides the basis for the duty personnel and analyzes the cause of the accident, as shown in the following figure:
Alarm function real-time query
Parameter meter reading function, mainly to query the electrical parameters of the low-voltage outgoing circuit. Supports electrical parameter query at any time, with functions such as data export and report printing. This report queries the electrical parameters of the low-voltage circuits in and out of the power distribution room of the low-voltage system of Inner Mongolia Meng Niu Dairy (Group) Co., Ltd., which mainly includes three-phase current, active power and active power. Each circuit name of this report is associated with the database, which is convenient for users to modify the circuit name. As shown below:
Electric parameter meter reading
Power consumption report function, select the time period for query, support the cumulative query of the power consumption at any time period, and have the functions of data export and report printing. Provide accurate and reliable electric energy report for the staff on duty. Each circuit name of this report is associated with the database, which is convenient for users to modify the circuit name. As shown in the figure below, the user can print the report directly, and save it to another location in EXCEL format. As shown below:
A schematic diagram of the system communication structure, which mainly shows the network structure of the system. The system adopts a hierarchical distributed structure and monitors the communication status of the bay layer equipment. Red means communication is normal, green means communication failure. The figure below is a schematic diagram of the communication status of the
Communication structure diagram
In the application of today’s power distribution facilities, the power distribution safety of the project is very important. The application of the Acrel-2000 power monitoring system introduced in this article in Inner Mongolia Meng Niu Dairy (Group) Co., Ltd. can realize The real-time monitoring of power consumption can not only display the power consumption status of the loop, but also has the function of network communication, which can form a power monitoring system with serial server, computer, etc. The system realizes the analysis and processing of the collected data, real-time display of the operation status of the distribution circuits in the distribution room, pop-up alarm dialogs, voice prompts for load exceeding limits, and generates various electric energy reports, analysis curves, graphics, etc., which is convenient The remote meter reading, analysis and research of electric energy show that the system is safe, reliable and stable. It provides a true and reliable basis for the commercial plaza project to solve the electricity problem and has achieved good corporate benefits.
1.Solutions For Enterprise Micro-grid System 2020.02